Rainwater collection is often a good option in areas with regular rainfall and where traditional water sources (i.e. groundwater, surface water) are not available or contaminated. The following ‘how to’ guide comes from my experience implementing Rain Water Harvesting Systems (RWHS) in the Solomon Islands, where many coastal communities don’t have others options for water supply.
The components of Rain Water Harvesting Systems (RWHS)
All RWHS are made of a four elements: a catchment area, a collection system, a storage reservoir and a water collection point.
Your catchment area would normally be a roof. Impermeable ground-level surfaces can also be used to catch rainwater. However, water caught on ground-level surfaces is usually of lower quality than raised surfaces, due to factors including dirty soil, wild defecation, agricultural chemicals and solid and liquid waste. So I’ll focus this guide on raised surfaces, such as roofs.
As you can guess, the bigger your roof, the better your catchment. You want to ensure you have the maximum runoff, by reducing the evaporation and infiltration through the roofing material. The runoff coefficient of a corrugated iron sheet is around 0.8 while for thatch it is 0.2. In Solomon Island, we used public buildings (i.e. schools and churches) for rainwater catchment and few private houses when we didn’t have any other option, making sure that it will be a shared RWHS. We even rehabilitated some of the roofs, using locally available corrugated sheets.
The collection system is made of gutters, placed on one or two sides of the roof, depending on its design. Always keep in mind that you want to get a maximum supply. In Solomon Islands, for gutters we used PVC spouting 150mm width and for downpipes PVC Ø100mm; which are the most common, the easiest to use and allowing a good water collection (limited losses of water and reduced frictions). Then, before the inlet of your reservoir, you need to install a 1st flush pipe – which is simply a vertical closed PVC pipe. The 1st rain will clean your roof and fill this flush pipe with dirty water rather than your reservoir. Quite useful.
The storage reservoir. It could be constructed – using local knowledge and skills, or bought fully equipped, installed outside, inside or even put underground. The local conditions, habits and expectations would guide you. Involve the concerned people during the assessment and design phases. But the reservoir capacity needs to be properly estimated, in order to store enough water for the dry season.
You can place the water collection point wherever you want, directly on the reservoir or further down, or even inside the house. The storage reservoir could also be put underground, with a pump would be needed to lift the water to where it is needed.
Design of the RWHS
Firstly, check if there is enough water to satisfy the demand, comparing the maximum water supply and the maximum demand of water. Then, calculate the required volume of the water storage ... (more)
This thread is public, all members of KnowledgePoint can read this page.